The Drive Unit
The barrier is driven by a torque motor. The torque motor is designed for alternating current and does not require limit switches nor a friction clutch. Its maintenance-free and can be stalled in any position without causing any damage to the motor. The barrier is factory wired, tested, ready to connect and supplied with all necessary mounting accessories.
The housing is manufactured from 2 mm zinc plated sheet then phosphate and powder coat finished for maximum protection against corrosion. The housing is supplied in a White Gloss finish as standard. Other colours are available on request, at extra cost.
Barriers may be supplied with the barrier boom fitted to either the right or left hand side. The barrier boom is a round profile of 75 x 1.6 mm and finished with a white powdercoat then applied with bright red reflective tape strips.
- Drive Unit
- Torque Motor
- Voltage 240 Volt
- Frequency 50 Hz
- Power Consumption 120 Watts
- Open / Close Time 5 sec average but approx 1 sec per mtr length of arm.
- Maximum Boom Length 6000mm
- Housing: Height 1000mm
- Width 300mm
- Weight 45kg
- A 10amp circuit breaker situated in the supply switch board.
- 2.5mm 2 core and Earth cable (TPS or Circular Orange) as the supply cable.
- 32mm conduit to run the cable from the switch board to the boom gate circuit breaker.
- Loop detectors
- Safety curtains
All our technical and sales staff are trained to assist in the installation of the safest automation systems available.
Product Data: Submit Manufacturer’s product data for all gate equipment including:
- Manufacturer’s standard details and fabrication method.
- Data on finishing, hardware and accessories.
- Recommendations for maintenance and cleaning of exterior finish surfaces.
Shop drawings for boom gate and installation are required from manufacturer, including:
- Layout and installation details.
- Footing details.
- Wiring diagrams
Installer qualifications: Engage an experienced boom gate installer who has completed installations of all equipment similar in design and extent to those required for the project and whose work has resulted in construction with a record of successful in service performance.
Manufacturer’s qualifications: Provide all boom gates produced by a firm experienced in manufacturing boom gate systems that are similar to those indicated for this project and that have a record of successful in service performance. All boom gates must be tested.
Single source responsibility: Obtain all boom gates from a single manufacturer, to ensure full compatibility and warranty of parts.
Design criteria: The drawings indicate the size, profile and dimensional requirements of all boom gates required and are based on the specific types and models indicated.
Delivery storage and handling
Deliver all gates and related components in the manufacturer’s original protective packaging. Do not deliver boom gates until the work is ready for their installation.
Inspect components for damage upon delivery. Unless minor defects in metal components can be made to meet the Architect’s specifications and satisfaction, damaged parts should be removed and replaced.
Field Measurements: Check opening by accurate field measurement before fabrication. Show recorder measurements on shop drawings. Coordinate fabrication schedule with construction progress to avoid delay of the work and possible damage to the finished product.
Where necessary, proceed with fabrication without measurement and coordinate fabrication tolerances to insure proper fit.
Basis of design: Design is based on gate type, manufactured by Leda Security Products Pty Ltd
Accessory Fittings: Provide manufacturer’s standard accessory fittings of the type indicated. Comply with requirements indicated for kind and form of metal and finish of gate fittings.
Anchors and Fasteners: Manufacturer’s standard anchors and fastenings.
Cold Gal: Can be applied to gate to help reduce oxidization of surfaces that need to be cut or welded during the installation process.
General: Fabricate all boom gate components to designs and sizes indicated. Sizes of gate and profile requirements of fittings and hardware are indicated on the drawings.
Prefabrication: Complete fabrication, assembly, finishing, hardware application and other work to the greatest extent possible before shipment to the project site. Disassemble components only as necessary for shipment and installation.
General: Automation of boom gates if required will be to required operation standard based on top or mid tier equipment. Top tier relating to automation equipment with the boom gate arm weight, speed and operation frequency well within specification. Mid tier relating to less stringent or frequent operating environments.
Standards: Equipment is to comply with all relevant and electrical and safety for the legal jurisdiction of installation.
Examine footing with the installer, present for compliance with requirements indicated, installation tolerances and other conditions that affect the installation of all gates such as wind loadings.
Correct unsatisfactory conditions before proceeding with the installation.
Do not proceed with installation until unsatisfactory conditions are corrected.
Install boom gate and associated components in accordance with manufacturer’s printed instructions and recommendations.
- Verify units level, plumb and true line.
- Lubricate hardware and other moving parts.
Concrete and reo foundation design must be certified by a qualified structural engineer to meet relevant portions of the Building Code of Australia and relevant Standards Australia codes for structural adequacy in particular AS 1170, AS 2870, and AS 3600.
- Adjust boom gate to provide a tight fit at meeting points.
- Hardware: Adjust operating hardware to ensure proper operation.
Clean boom gate surfaces after installation, exercising care to avoid damage to the finish.
Institute protective measures required throughout the remainder of the construction period to ensure that the all boom gates do not incur any damage or deterioration, other than normal weathering, at the time of acceptance.
Boom gate and warranty to be not less than 12 months on installation but otherwise as per contract or manufacturers warranty.
Maintenance is to be based on frequency of use and to be as per manufacturers maintenance manuals to be supplied with equipment. Supplier must maintain offices within the state of installation.